Filed under: Uncategorized | Tags: Davis Besse, electricity generation, energy, nuclear accident, nuclear energy, nuclear power, power generation, radiation leak
While we’re on the subject of super old and leaky nuke plants. This plant’s near Toledo, and is also up for a controversial license renewal.
During the performance of MODE 3 engineering walkdown inspections in accordance with procedure DB-PF-03010 (ASME Section III, Class 1 and 2), with the RCS at Normal Operating Temperature and Pressure, a pressure boundary leak was identified on the Reactor Coolant Pump (RCP) 1-2 1st seal cavity vent line upstream weld of 3/4 inch small bore pipe socketweld at a 90 degree elbow between the RCP pump and valve RC-407 (1st Seal Cavity Vent Isolation). The plant was in MODE 3 at Normal Operating Pressure and Normal Operating Temperature (NOP/NOT) for the inspections.
“The plant entered Technical Specification (TS) Limiting Condition for Operation (LCO) 3.4.13, ‘RCS Operational Leakage,’ Condition B and procedure DB-OP-02522. ‘Small RCS Leaks,’ abnormal operating procedure. Plant cooldown to comply with LCO 3.4.13, Condition B, Required Action B.2 is in progress. The cause and resolution are under evaluation.